Product Specifications. • 9th edition approved UL • Capacity of up to 64 panels with zones of programming through software. • Powerful and versatile . FireNET FN/FN UL/FM approved. Expandable loop and connect to other panel. ANALOG ADDRESS FIRE CONTL PAN, Hochiki. Description: Analog Address Fire Contl Panel; Category: Addressable Panels, Fire Control Panels, Fire; UPC.
|Published (Last):||11 February 2014|
|PDF File Size:||2.7 Mb|
|ePub File Size:||8.81 Mb|
|Price:||Free* [*Free Regsitration Required]|
While studying the installation manual of firenet analog addressable system there are something confused me. Then the horns connected with the power supply get power from this external power supply when the relay gets power from NAC.
Why SOM is used? I don’t know i am right or wrong. Up to devices can be placed on a single SLC loop.
HOCHIKI – Soluparts
Am i right or wrong please explain. As it says in the manual about the SOM: Search engine Use this form to find things you need on this site. Also i know that will not supervised. Can hochikki give me a diagram of your suggestion? Will this connection work? They can be installed remotely in the building so wire distance and voltage drop issues are reduced.
If hocchiki use a automatic Sprinklers system then the basic is if there is a fire then detectors detects and send a signal to control panel that there is a fire, then control panel send a signal to notification devices to alarm. What is the principle of Supervised Output Module?
Events are reported to a compatible central station monitoring receiver. Post Sun Mar 05, 6: That’s why i am confused.
The device address is hohiki stored on an onboard. Keep in mind the power available for NACs is limited. Post Mon Mar 20, But I dont want to use som also Fj-2127 want to install many horn within a panel which will work automatically. Flexible Grooved Coupling – Series. These outputs may be used for a variety of purposes including door holders, elevator recall, and other fire safety functions. From the Firenet installation manual: According to the manual I downloaded there is an addressable manual station.
The communicator may be configured to report by zone or by address point.
ANALOG ADDRESS FIRE CONTL PAN
That means 4 NACs at 1 amp each. Then there should be a module to control Sprinklers system and a signal should be sent to that module from a control panel to activate the Sprinklers. Dome Camera p Turbo HD, 2. Mostrando 19—36 de 90 resultados Orden predeterminado Ordenar por popularidad Ordenar por novedades Ordenar por precio: Post Sun Mar 05, 3: Post Mon Feb 27, 5: Yes, this would be the SOM.
I do not know if it is acceptable on your particular job site. Post Mon Mar 20, 6: Because the NAC extender has its own power supply it does not draw power from the main panel. To use a standard contact type call point there is a selection of modules shown in the manual.
All Rights Reserved In the control panel there is 4 NAC connection points. Post Sun Mar 19, 6: It provides two independent contact monitoring circuits while only utilizing one address on the SLC loop. Any power consumed by devices connected to a SOM powered by the panel is also part of that 4 amps.
The FNSLC can be added at the factory or installed in the field, and mounts within the main control board location as a piggy-back board. This has to be decided by knowing what is connected to each SOM, how much current is being used, and if that is in the capability of the power supply.
One NAC at 1. Can i directly connect sounder base in a SLC loop? Post Thu Mar 02, 1: I know that if I use som module then I can fn-21127 many fn-2172 within a panel.
I don’t have any practical experience.
User Control Panel Profile Logout. I am very beginner in fire detection system. NAC only can supply 4 amp only.