View and Download Dixell XR20C installing and operating instructions online. Digital controller with off cycle defrost. XR20C Controller pdf manual download. View and Download Dixell XR20CX installing and operating instructions online. Digital controller with off cycle defrost. XR20CX Thermostat pdf manual. QVWDOOLQJ DQG 2SHUDWLQJ,QVWUXFWLRQV Digital controller with off cycle defrost. SET: To display target set point; in programming mode it selects a.
|Published (Last):||22 February 2007|
|PDF File Size:||12.72 Mb|
|ePub File Size:||9.68 Mb|
|Price:||Free* [*Free Regsitration Required]|
Defrost is performed through a simple stop of the compressor.
To display target set point; in programming mode it selects a parameter or confirm. Push and immediately release the SET key: Installing and Operating Instructions. DOWN To see the min stored temperature; in programming mode it browses the.
The instrument is fully configurable through special parameters that can be easily.
In case of failure or faulty operation send the instrument back to the distributor or to. Page 2 Energy Saving cycle. Each LED function is described in the following table.
To change the Set value push the 9 or 8 arrows within 10s. Model XR20C, format 32 x 74 mm, is a digital thermostat with off cycle defrost designed for. The digital input can operate as. To print the manual completely, please, download it. dixfll
Instrument XR20CX shall be mounted on vertical panel, in a 29×71 mm hole, and fixed using the special bracket supplied. By pressing the 9 key again or by waiting 5s the normal display will be restored. Fit the probe where it is not accessible by the End User.
The instrument must not be. Consider the maximum current which can be applied to each relay see Technical Data. This manual is part of the product and should be kept dixfll the instrument for easy and. Parameter “IdF” controls the. Got it, continue to print. Page 4 Ptb Map code Dixell S.
The instrument shall not be used for purposes different from those described hereunder. By pressing the 8 key again or xg20c waiting 5s the normal display will be restored. XR20CX panel mounting in a 71x29mm panel cut-out Protection: Ensure that the wires dizell probes, loads and the power supply are separated and far.
The “Lo” message will be displayed followed by the minimum temperature recorded. Push and immediately release the SET key or wait for 5 seconds to. Push the DEF key for more than 2 seconds and a manual defrost will. Comments to this Manuals Your Name.
Dixell XR20CX Installing And Operating Instructions
The “Hi” message will be displayed followed by the maximum temperature recorded. In case of fault in the thermostat probe the start and stop of the compressor xr2c timed through. Check the supply voltage is correct before connecting the instrument.
CCS Set point for continuous cycle: Hold press the SET key for more than 3s, while the max. Enter text from picture: Don’t show me this message again. Do not expose xrr20c water or moisture: To see the max.
electronic controller DIXELL XR20C-5N1C1 378018
Push the SET key for more than 2 seconds to change the Set point value. Add to my manuals Add. By pressing ‘print’ button you will xr20cc only current page.
Ptb Map code Dixell S. To confirm the operation the “rSt” message starts blinking and the normal temperature.
Dixell XR20C Electronic Digital Refrigeration Temperature Controller | eBay
Page of 4 Go. Don’t have an account? In case of applications in industrial environments, the use of mains filters our mod. To memorise the new set point value push the SET key again or wait 10s. It provides a relay output to drive the.